Heat line C24 Pdf User Manuals. View online or download Heat line C24 Installation, Servicing And User Instructions Manual. The boiler’s ‘Log Book’ must be completed at each Service visit. By means of a manual switch the C24/C28 can be set to operate in one of two operating modes, . Boiler Manuals for the Heatline Compact C24 appliance.
|Published (Last):||9 July 2005|
|PDF File Size:||5.76 Mb|
|ePub File Size:||10.41 Mb|
|Price:||Free* [*Free Regsitration Required]|
Open the isolating valves on the low and return connections.
Disconnect heatllne electrical leads from the fan 4. Verify the operation of the condensate pump F83 No water in the installation: Isolate the appliance 2.
Heatline Compact C24
Verify the fuses connections. Verify the wiring harness. Disconnect the electrical leads and air pressure switch connection tube from the fan. Make sure that all electrical connections are fit into the right home. A delay up to 45 sec may be observed- depending on heatline c24 manual model. Make sure that all used washers are replaced if heatlune 7. Remove the air pressure switch by pulling forward off its bracket heatline c24 manual.
Fluctuation of flame signal.
HEAT LINE C24 INSTALLATION, SERVICING AND USER INSTRUCTIONS MANUAL Pdf Download.
To arrange parts replacement contact Heatline customer service specialists by explaining what is being requested, providing an error message if any appears on the LCD display.
Re-assemble the boiler in reverse order 7. Verify the flow and return cc24 sensor connection. The hydraulic circuit now needs to be drained heatline c24 manual.
Rotate the gas pipe and withdraw gas valve heatline c24 manual 9. That can be achieved by fitting dip switch number 5 into the position ON. Re-set if necessary the dip switches and the potentiometers to values of the old PCB 8.
Re-assemble the boiler in reverse order.
Re-connect sensing tube and all the electrical leads 7. Fit the new fan following reverse order logic.
That can be achieved by fitting dip switch heatline c24 manual 5 into the position ON — 45 seconds delay: Verify the igniter unit F28 Ignition fault Verify heatline c24 manual return gas circuit gas valve open. A volt, duel speed fan expels combutsion products from the chamber to outside air via an associated flue system.
While doing this lift the panels up 5. Replace gas supply, pressure or healine valve.
Heat Line C24 Installation, Servicing And User Instructions Manual
Re-assemble the boiler in reverse order Secondary Heat Exchanger replacement 1. Verify the boards reference. Disconnect the electrical leads of low pressure sensor 8.
Verify the gas valve connections. Boiler parts Each Heatline boiler is equipped with following additional parts: Pull forward the heat exchanger and remove Whenever the pressure heatline c24 manual on the gauge is higher then 1.
Permanent temperature heatline c24 manual between flow and return heating sensors. Fit the replacement sensor in reverse order of removal ensuring all washers are fitted 6.
Locate the central heating sensor — it is on left side of the combustion chamber on the outlet of the primary heat exchanger as shown on the picture below 4. Heatline c24 manual the chamber cover by releasing all the screws should be two on each side.
Make sure that the sensor is clipped to the tube.